Products

Home / Products

Boiler Horsepower What is the boiler horsepower of a boiler generating 21,500 lbs of steam per hour at 155 psi? The factor of evaporation is 1.08. BHP = (LB/HR*fe)/34.5 BHP Boiler Horsepower BHP = (LB/HR*fe)/34.5 Lb/Hr Pounds per Hour BHP = 21500 * 1.08 / …

10 Common Boiler Formulas STATIC HEAD PRESSURE What is the static head pressure of a boiler operating at 275 psi? SHP = Bpr * 2.31 SHP = Bpr * 2.31 SHP = 275 * 2.31 SHP = 635.25 Where, SHP static head pressure Bpr boiler pressure (psi) 2.31 multiplier STEAM PRODUCED How much steam will a 150HP boiler make in 2.5 hours? S = HP * 34.5 * T

saturated steam temperatures pressure table steam temperature. created date: 10/24/2012 5:43:28 pm

›› Quick conversion chart of psi to bar. 1 psi to bar = 0.06895 bar. 10 psi to bar = 0.68948 bar. 20 psi to bar = 1.37895 bar. 30 psi to bar = 2.06843 bar. 40 psi to bar = 2.7579 bar. 50 psi to bar = 3.44738 bar. 100 psi to bar = 6.89476 bar. 200 psi to bar = 13.78951 bar ›› Want other units?

Jul 03, 2019· Q: What is the formula to convert steam temperature into pressure? The question asks for a formula so here is a very good estimate that is good enough for most purposes. Saturated steam temperatures and pressures are related by a power curve relat

STEAM EQUIPMENT CONVERSION US · UK · METRIC · SI UNITS FOR THERMAL ENGINEERS FLUIDS & FLOW 1 bar = 14,50 psi 1 bar = 100,0 kPa 1 bar = 0,9869 Atm. 1 mbar = 0,7501 mmHg | Torr 1 Boiler HP = 15,65 kg steam /h Specific Heat 1 kJ/(kg·K) = 0,2388 Btu/(lb·°F)

Boiler Pressure & Steam Temperature Chart . Bar Litres (boilers up to 2 gallons) To use the Bar Litre Charts first select the page applicable to the water capacity. of the boiler (the water capacity is when the boiler is completely full not the. capacity when the water is half way up the glass) then find the working. pressure of the boiler in

Often it is necessary to convert a measure of capacity from one term to another. The conversion table will allow you to quickly convert various measures of capacity. The table and formulas can help you size and pick out components such as condensate pumps and boiler feed pumps. Some additional conversion factors that may prove helpful are shown below.

Convert ACFM to SCFM SCFM = ACFM x (Pounds Per Square Inch Gauge + Atmospheric Pressure) x 528 (Temperature of Air Inlet + 460) x Atmospheric Pressure SCFM = ACFM x PSIG + 14.7 x 528 T1 + 460 x 14.7 Steam Required (lbs / hr) lbs / hr = Btu per hour Enthalpy of Steam at Operating Pressure lbs/hr = Btu/hr Btu/lb F s or Btu / lb oF F s =

in the boiler drum. This can be calculated as follows: E = Evaporation or steam generation rate. S = Amount of solids (ppm) B = Blow down (m3 / hr) C = Maximum permissible concentration of solid inside the boiler drum B = E x S (m3 / hr.) C – S % B = S C – S This formula has been equally applied to control individual constituents in boiler.